INSTALL SWASHPLATE ROTATING RING INTERRUPTER BRACKETS
Install brackets (6) on rotating ring (4) by hand.
Check that clearance between end of brackets
(6) and rotating ring (4) is 0.150 inch.
Apply pressure to seat each bracket and squeeze
out excess adhesive. Make sure brackets do
Wipe excess adhesive from brackets. Use cloth
(E120) damp with methyl-ethyl-ketone (E244).
Wear gloves (E186).
Cure adhesive at 150 to 160 F (66 to 71 C) for
2 hours. Use heat lamp. Monitor temperature.
Use temperature indicating strips (E413).
Curing time increases rapidly as
temperature decreases. Adhesive
(E43 or E47.1) will not cure below
60 F (15 C). Do not count as cure
time any period when temperature is
below 70 F (21 C).
If heat lamp is not available, a
serviceable cure can be achieved
at 70 to 80 F (21 to 27 C) in 24
Coat lip of seal (11) and running surface (12) on
stationary ring (3) with grease (E190).
Install rotating ring assembly (4) on stationary
ring (3). Use a mallet, if needed.
17.1. Position bracket (6) over phase detector (6.1)
by turning rotating ring (4) by hand. Check
clearance between each of the three interrupter
brackets (6) and phase detector (Magnetic
Pickup (6.1)). Clearance should be 0.015 to
END OF TASK